The Best Restaurant kitchen Hood fire Suppression System
• The Best Hood fire Suppression System Installation & Service
M&E Best Fire Protection provides the best Restaurant and kitchen hood fire suppression systems that are required by law to be inspected, serviced, tested and certified at semi annual intervals. We always supply services and products that are high quality. M&E Best Fire Protection, Inc. is your source for Kitchen Hood / Restaurant Fire Systems in the greater Los Angeles & San Fernando Valley areas. Your safety and satisfaction is our number one priority.
The grease from cooking accumulates in hard to reach places of the hood, plenum, and ducts, and that grease is a fire hazard for it is combustible with high temperatures. Therefore, hood cleaning is recommended to be performed quarterly to ensure proper functioning of the fire system and to maintain the Health Department standard and as required by the National Fire Protection Association (NFPA) #96 in accordance with Table 11.3 Inspection of Exhaust System. We perform hood cleaning and exhaust cleaning with special equipment to remove grease from hard to reach places to leave your hood sparkling clean and not to mention free of grease combustion.
Please give us a call if you have any questions and we will be happy to provide you with a quote. (888) 702 – FIRE- (3473)
Our Hood Fire Suppression System & Fire Extinguishers experts provide planning, installation, maintenance, repair and testing for all types and brands of our fire protection equipment. Our technicians our licensed and certified to service Ansul, Pyro Chem, Protex II, Range Guard, Amerex, Buckeye fire system.
We install, service, and repair automatic hood fire suppression system and industrial fire systems, according NFPA 96, 17&17A, and local authority having Jurisdiction. Pre-engineered fixed extinguishing systems also known as automatic extinguishing systems and/or fire suppression systems shall be serviced at least semi-annually and immediately after system activation according to OSFM Laws and Regulations for Automatic Extinguishing systems 2009 Edition Article 4 section 904. click here
Restaurant UL-300 Fire Suppression Systems Installation:
Today’s commercial cooking environments require the use of hotter burning vegetable oils. This, coupled with highly insulated, slow-cooling appliances have increased the difficulty of extinguishing fires in such kitchens. As a result, the California State Fire Marshal adopted the UL-300 2007 California Fire Code section 904.11 which requires that all existing dry-chemical and wet-chemical extinguishing systems shall comply with UL-300 no later than the second required servicing of the extinguishing system following the effective date of the regulation (January 1, 2008).
We are certified to service, repair, install and sell UL-300 restaurant automatic fire extinguishing systems. Experience is extremely important when choosing a company to install a fire system. Our company has been in business for over fifteen years servicing and installing fire suppression systems to several hotels, large chain restaurants, family owned restaurants, universities, and body shops. We have dealt with countless county, city, and fire department inspectors and our inspections aare guaranteed to be successfully passed within the accorded time frame. We install only the highest quality of kitchen hood fire suppression systems and we are certified installers of Pyro Chem, Protex II, Amerex, and Buckeye fire suppression systems.
Our Scope of Work Includes:
• Professional plans design and submission to the city for approval.
• Complete fire system installation upon plans approval.
• Electrical connection to micro-switch to shut off all electrical power that produce heat (light bulbs, receptacles, electrical switches under the hood, as well as the make-up air (swamp cooler) and/or fire alarm system, if provided) (NFPA 17A, 4.4.3. & 22.214.171.124)
• Gas valve installation (if required).
• Fire Department final inspection.
We guarantee a professional and prompt culmination of the job so you may not lose any of your valuable business time. We guarantee high quality products with the most competitive prices on the market and a friendly staff that will accompany you with any inquiry from start to finish.
Indications to determine if your fire system is NOT UL-300 compliant:
• If your fire protection system is powder.
• If your fire protection system is wet chemical and was manufactured after November 21, 1994.
• The local enforcement authorities, fire department, insurance company, fire protection company, or other authority requires/recommends upgrading the system.